Check with that product’s installation sheet for instructions. Twist and take away mounting bracket to insert battery. Product Description Lutron’s ceiling-mounted Occupancy Sensors are wireless, battery-powered, passive infrared (PIR) devices that mechanically management lights through RF communication with a dimming or switching device. These Sensors detect the heat from individuals shifting within an area to find out when the space is occupied. The Sensors then transmit the suitable commands to the associated dimming or switching device to turn the lights on or off routinely, providing each comfort and distinctive power financial savings. Sensor does not carry out satisfactorily from this location, it could also be moved to 1.4 Ifanother location by pulling the Sensor straight down and repeating steps 1.Three and 1.4. 1.5 If the Sensor’s efficiency is satisfactory, it ought to be completely attached to the ceiling tile, as described in part G. Permanent Mounting. Non permanent Solid Ceiling Mounting Use this procedure if the Sensor will likely be mounted on a solid, steady ceiling surface resembling drywall, plaster, concrete, or wood. Two 3M™ Command™ adhesive strips are provided for briefly mounting and testing the Sensor on easy, solid ceiling surfaces. These strips are designed for straightforward, damagefree removing and will not be reusable. These strips should not be used for completely mounting the Sensor (see section G. Everlasting Mounting ). Rigorously comply with the elimination directions beneath to ensure the ceiling is not broken throughout elimination. Notice: Do not use the adhesive strips on ceiling tiles, as they'll likely trigger damage to the tile upon elimination. Simple-to-follow Instructions Set-Up In order for the Sensor to operate properly, it must first be set up with a corresponding dimming or switching machine. The procedure for establishing a Sensor with a Maestro Wireless® (MRF2- only) Dimmer or Digital Switch is detailed under. P/N 041-172a 2.1 Peel the red "Command Strips" liner off of one of many adhesive strips and apply the strip to the flat facet of the mounting bracket as proven in the diagram. Note: Don't cowl the bracket’s screw holes because they will be used to mark screw hole places on the ceiling. Establishing a Sensor with a Maestro Wireless Dimmer or Digital Change Dimmer Key Features · Low Maintenance. 10-12 months battery life. Handy low-battery indicator. · A number of Devices. Up to three Sensors can work together to regulate lights for broader protection in large areas. Each Sensor may be added to as much as 10 receiving devices. Sensor Operation Occupancy Version - The Sensor will automatically flip the lights on when the space is occupied and mechanically turn the lights off after the house is vacated. The Sensor will mechanically turn the lights off after the space is vacated. There's a constructed-in 15-second vacancy grace period that begins when the lights are automatically turned off, during which the lights will mechanically turn again on in response to movement. This grace interval is offered as a security and comfort function in the event that the lights flip off while the room is still occupied, in order that the consumer doesn't need to manually flip the lights back on. After 15 seconds, the grace interval expires and the lights should be manually turned on. This Sensor is part of a system and can't be used to regulate a load with no compatible dimming or switching system. Discuss with the instruction sheets of the receiving device(s) for set up data. The Sensor could also be installed up to 60 ft (18.3 m) away from the related dimming or switching system(s) if they are in direct line of sight. If there are partitions or different barriers between the Sensor and receiving machine(s), the Sensor ought to be located within 30 ft (9.1 m). Warning: This product must not be used to manage equipment which could create hazardous conditions, resembling entrapment, if operated accidentally. Sensor in a location the place it has a broad view outside the intended space. If this is unavoidable, the lens will be masked to dam the view of undesired areas (consult with part I. Lens Masking). This warranty is in lieu of all other categorical warranties, and the implied warranty of merchantability is restricted to at least one yr from buy. This guarantee does not cowl the price of installation, removal or reinstallation, or harm ensuing from misuse, abuse, or damage from improper wiring or set up. This guarantee doesn't cover incidental or consequential damages. LUTRON’S Legal responsibility ON ANY Claim FOR DAMAGES ARISING OUT OF OR IN CONNECTION WITH THE MANUFACTURE, SALE, Set up, Delivery, OR USE OF THE UNIT SHALL By no means EXCEED THE PURCHASE Worth OF THE UNIT. This warranty gives you specific authorized rights, and you may have other rights which range from state to state. Some states do not allow the exclusion or limitation of incidental or consequential damages, or limitation on how lengthy an implied warranty might last, so the above limitations might not apply to you. Patents pending. Lutron, Maestro Wireless, and the Sunburst brand are registered trademarks and Radio Powr Savr is a trademark of Lutron Electronics Co., Inc. ANSI is a registered trademark of the American Nationwide Requirements Institute. IEC is a trademark of the International Electrotechnical Commission. Made and printed in the U.S.A. 25/09/09 P/N 041-172 Rev. A 8 ft (2.Four m) 18 x 18 ft (5.5 x 5.5 m) 13 ft (4.0 m) 9 ft (2.7 m) 20 x 20 ft (6.1 x 6.1 m) 14.5 ft (4.Four m) 10 ft (3.Zero m) 22 x 22 ft (6.7 x 6.7 m) 16 ft (4.9 m) 12 ft (3.7 m) 26 x 26 ft (7.9 x 7.9 m) 19 ft (5.Eight m) Short-term Mounting Methods 1.1 1.2 Insert the ceiling tile mounting wire by the two smaller holes in the mounting bracket and change the mounting bracket. Mount Sensor to a ceiling tile by inserting the wire legs by the tile, ensuring the Sensor is flush to the tile. Be aware: Don't twist wire legs together. 1.2 After the Sensor has been briefly mounted, leave the Sensor in place on the tile and either take the tile down or take away an adjacent tile to gain access to the legs of the mounting wire on the back of the tile. Low Exercise: This is essentially the most delicate setting and will detect very slight motions. This is the advisable setting, as it should work nicely for practically all applications. It is good for spaces the place occupants will usually be seated for long intervals of time. Twist the wire legs together tightly so the mounting bracket stays snug towards the tile. This setting is barely much less sensitive than the Low Activity setting and can be used for areas that expertise regular exercise. This is the least delicate setting and can be utilized for areas that may typically only experience giant motions, resembling foot site visitors. The Low Exercise setting is the default and will carry out greatest for many applications. Hardly ever, if the Sensor is positioned near external noise sources similar to heating vents, air conditioning vents, or gentle bulbs, it may flip the lights on without occupancy or keep the lights on too lengthy after vacancy. If this happens, changing the sensitivity to Medium Activity or High Activity should resolve the issue. Replace the tile. Permanent Strong Ceiling Mounting 2.1 2.2 2.3 Superior Set-Up Operation The superior set-up is accessed through the use of the buttons on the again of the Sensor. Drill two 3/16 in (4.6 mm) pilot holes for the offered screw anchors. Press the anchors into the holes and tap flush with a hammer. To show the current setting, press and launch the specified button. An LED will illuminate briefly, indicating the current setting. Place the flat side of the mounting bracket towards the ceiling and install the 2 provided screws using a hand screwdriver. To regulate a setting, press and hold the specified button till the LED corresponding to the current setting begins flashing quickly, indicating the setting can now be adjusted. Each subsequent button press of less than 2 seconds will increment the mode to the subsequent out there setting. Urgent any of the opposite buttons will have no effect. To save the chosen setting, press and hold the button until the LED turns on solid, indicating the saved setting. Through the adjustment procedure, if there isn't a exercise for 30 seconds, the LEDs will flip off and no settings shall be saved. Word: Don't over-tighten. 2.4 Attach the Sensor to the mounting bracket by inserting and twisting in a clockwise path until the Sensor locks into place. To take away the bracket from the ceiling, grasp the elimination tab on the adhesive strip and pull the tab VERY SLOWLY straight throughout the ceiling, stretching the strip until the bracket releases from the ceiling. Discard the strip. By no means pull the strip at an angle, as it might break or injury the ceiling surface. Notice: Do not pull at an angle. Lens Masking (Non-obligatory) Whenever possible, the Sensor must be put in in a location where it can not easily see into areas exterior the meant space, similar to hallways or adjoining rooms. If this situation can't be avoided, portions of the lens could also be masked with the provided labels to dam the Sensor’s view of the undesired areas. It is strongly recommended to take away the Sensor from the mounting bracket earlier than making use of Advanced Set-Up (Elective) the masking labels. The Sensor options a number of superior set-up modes. For the vast majority of installations, the default settings will present the most effective efficiency and also you is not going to have to utilize the superior set-up. The Occupancy model of the Sensor has three adjustable superior set-up modes: Timeout, Auto-On, and Sensitivity. The Vacancy-Solely model has only two modes (Auto-On not available). The default settings are listed below. The Sensor will be screwed onto the mounting bracket in several totally different orientations. Be sure to notice the Sensor’s orientation earlier than taking it down and exchange the Sensor in the same orientation to ensure the meant space gets blocked. Outer lens sections correspond to the detection areas furthest away from the Sensor, while inner sections correspond to areas closer to the Sensor. Watch out when making use of the labels to avoid creating gaps between adjacent masked sections. The Sensor could detect motion through inadvertent gaps. Always (Occupancy version only) Timeout 30 min 15 min 5 min Auto-On All the time Low light Disable Activity Timeout 30 min 15 min 5 min Superior Set-Up Modes Auto-On All the time Low mild Disable Exercise Activity: Low Exercise Lens sections proven in white are masked with labels Timeout The Sensor will flip the lights off if no movement happens throughout the timeout interval. There are three available timeout settings: 5, 15, and half-hour. Lens Mask Lens sections proven in gray have not been masked Auto-On The computerized-on functionality of the Sensor may be adjusted to manage how the lights respond upon preliminary occupancy. There are three out there settings: All the time, Low mild, and Disable. Always: The lights will always turn on. Testing Sensor Coverage With the Sensor mounted on the ceiling, press and release the "Test: Sensor" button on the entrance of the gadget. The lens will glow briefly, indicating the test mode has been entered. Be aware: There's a warm-up period of approximately 40 seconds after the batteries are put in before the test mode can be activated. If the button is pressed throughout this time, the lens will flash continuously until the warm-up interval is full, and then the take a look at mode can be automatically entered. Affirm the coverage area by strolling via the area and observing the lens. The lens will glow stable every time motion is detected. If the lens remains off during motion, the Sensor can't detect movement at that location. Press and release the "Test: Sensor" button once more to exit the take a look at mode. If the button shouldn't be pressed, the test mode will robotically day trip 15 minutes after being enabled, or 5 minutes after the final detected movement if the room is vacated. If the Sensor has vital bother detecting movement during the take a look at, it should be moved to another location and retested. If the Sensor nonetheless has poor detection from the brand new location, discuss with the Troubleshooting part. Momentary Drop Ceiling Mounting Use this procedure if the Sensor can be mounted on a ceiling tile. The ceiling tile mounting wire is supplied for both temporary and everlasting mounting of the Sensor to drop ceilings composed of a number of tiles. It is designed to permit temporary mounting, testing, and repositioning (if necessary) of the Sensor without damaging a ceiling tile. As soon as the Sensor’s closing place has been chosen, the mounting wire may be twisted to lock the Sensor in place permanently. If the Sensor coverage and wireless communication assessments have been efficiently accomplished, use the mounting bracket as a template to mark the screw gap places with a pencil. Word: Pull very slowly. Max. Room Dimensions Radius of Coverage for Full Coverage at Flooring If you are unsure about accurately positioning the Sensor, the next non permanent mounting and testing procedures are recommended to verify proper efficiency before permanently installing the Sensor. Sensor’s detection range relies on the ceiling top, as shown in the table below. Notice: Do not disassemble, crush, puncture, or incinerate the batteries. Don't dispose of batteries in regular household waste. Please recycle, take to a correct battery disposal facility, or contact your local waste disposal provider regarding local restrictions on the disposal or recycling of batteries. O NOT mount the Sensor inside 4 ft (1.2 m) of HVAC vents or mild bulbs put in beneath the ceiling line. Warmer rooms may scale back the Sensor’s capacity to detect occupants. Use solely excessive-quality lithium batteries, size CR123, 3 V (ANSI-5018LC, IEC-CR17345). Do not use rechargeable batteries. Using improperly rated batteries might harm the Sensor. For questions concerning the installation or operation of this product, name the Lutron Technical Help Center. Please provide actual mannequin quantity when calling. U.S.A. and Canada (24 hrs / 7 days) Setting the Occupancy Light Degree (occupancy version, dimming devices only) the Sensor to the mounting bracket by inserting and twisting in a clockwise 2.5 Attach direction until the Sensor locks into place. Sensor coverage and wireless communication tests as described in 2.6 Perform sections E. Testing Sensor Coverage and F. Testing Wireless Communication. The Sensor needs to be installed in a location the place it has a very good view of all parts of the room. The Sensor requires line of sight to function correctly. If you can not see the Sensor, it can not see you. The Sensor can not see by glass objects akin to patio or shower doors. The vary and performance of the RF system is highly dependent on quite a lot of advanced factors corresponding to: · Distance between system components · Geometry of the constructing structure · Building of walls separating system elements · Electrical gear positioned close to system components Technical Help 2.2 Establish a location on the ceiling the place the Sensor could have a good view of the room. 2.Three Remove the black "wall side" liner from the adhesive strip. The Sensor is designed for ceiling use solely. Do not set up on ceilings greater than 12 ft (3.7 m) or non-ceiling surfaces. Doing so may significantly inhibit the Sensor’s performance. 4. Don't paint Sensor. · · · · The "Lights On" and "Lights Off" buttons should now switch the lights in the room on and off, respectively, when pressed. Repeat the above process to set up the Sensor with any extra units. The Sensor is intended for indoor use solely. Operate between 32 °F and 104 °F (zero °C and forty °C). 1.1 several seconds. Sensor that has been set up. After approximately 6 seconds, the lens will flash rapidly several instances, indicating the light degree has been saved. All Sensors arrange with the Dimmer will now use the saved occupancy mild level. 2. Clear Sensor with a gentle damp cloth solely. Do not use any chemical cleaners. Be aware: This equipment has been examined and found to adjust to the bounds for a class B digital system, pursuant to part 15 of the FCC rules. These limits are designed to supply affordable protection in opposition to dangerous interference in a residential set up. This equipment generates, makes use of and can radiate radio frequency energy and, if not put in and utilized in accordance with the instructions, could trigger harmful interference to radio and television reception, which might be decided by turning the tools off and on. The person is inspired to try to appropriate the interference by one or more of the following measures: Reorient or relocate the receiving antenna. Improve the separation between the tools and receiver. Connect the tools into an outlet on a circuit totally different from that to which the receiver is linked. Seek the advice of the supplier or an skilled radio/Television technician for help. Caution: Adjustments or modifications not expressly accredited by Lutron Electronics Co. may void the user’s authority to operate this gear. This gadget complies with Part 15 of the FCC guidelines. This device should settle for any interference obtained, together with interference that may trigger undesired operation. Swap 2.1 Set the Dimmer to the desired light level for getting into the room. 2.2 Save holding the "Lights On" button on the entrance of a Observe: For either Sensor model, the lights may also be manually turned off at any time through the use of the dimming or switching system immediately. Essential Notes or Add the Sensor to the Dimmer or Change by pressing and holding the "Lights Off" button on the entrance of the Sensor for approximately 6 seconds till the lens flashes briefly. The lights in the room will also flash three instances, indicating the Sensor has been successfully added. The Dimmer or Change will exit set-up mode automatically. The sensitivity of the Sensor may be adjusted based mostly on the anticipated degree of activity throughout the room. There are three accessible exercise settings: Low Exercise, Medium Exercise, and High Activity. Everlasting Drop Ceiling Mounting Observe: Leave the elimination tab exposed past the edge of the bracket so it can be accessed for elimination later. 6 seconds till all LEDs on the device begin flashing. Release the faucet button. Sensor is detecting motion in areas that aren't desirable, corresponding to hallways or adjoining rooms, check with section I. Lens Masking. If Sensor detection is passable during this test, carry out the wireless communication take a look at as described in part F. Testing Wireless Communication. Testing Wireless Communication This check must be carried out to confirm that the Sensor has been appropriately arrange with the corresponding dimming or switching device and that there is proper wireless communication from the chosen Sensor location. If the lights within the room are usually not on, turn them ON manually at the dimming or switching machine. Press and launch the "Lights Off" button on the entrance of the Sensor. The lights should flip OFF. Press and launch the "Lights On" button on the front of the Sensor. The lights ought to turn on. If the lights do not reply accurately, confer with the Troubleshooting part. Low mild: The lights will solely activate robotically upon entry if there is not already sufficient ambient mild in the room. Hallway falls inside Sensor’s coverage area. Disable: This setting converts the Sensor to vacancy mode. The lights is not going to routinely turn on but will still routinely flip off after vacancy. The lights should be manually turned on through the use of the related dimming or switching gadget. Observe: The 15-second vacancy grace period is energetic in this mode. Check with the Sensor Operation part originally of this doc for extra details. Troubleshooting Symptom Possible Causes Answer Lights don't activate when house is occupied. Sensor is just not correctly added to dimming / switching machine(s). Sensor’s Auto-On setting is about to "Low light" or "Disable". The lights have been just lately turned off manually and the timeout has not but expired. Sensor does not have full view of room. Sensor is outdoors wireless range of dimming/switching gadget. Discuss with part B. Set-Up. Confer with part H. Advanced Set-Up. Dimming/switching device has been improperly wired. Gentle bulb(s) burned out. Breaker is off or tripped. Sensor’s timeout is too brief for this software. Sensor does not have full view of room. Lens mask is improperly utilized. Sensor’s sensitivity is too low. Sensor’s timeout has not but expired. An exterior noise supply akin to an HVAC vent is interfering. Seek advice from section A. Pre-Installation. Habits of lights does not match Sensor settings. Sensor protection extends past room perimeter. The meant setting was not saved. A number of Sensors are added to a dimming/switching system and their settings don't match. Refer to section A. Pre-Installation. Confer with section C. Sensor Placement or I. Lens Masking. Discuss with part H. Superior Set-Up. Seek advice from part H. Superior Set-Up. Sensor lens doesn't glow in response to movement during Sensor coverage testing. Sensor can not see motion attributable to obstruction. Room is too big or oddly shaped. Transfer Sensor to another location. Seek advice from part C. Sensor Placement. Multiple Sensors may be necessary for full room protection. Strive transferring Sensor to a new location or lowering sensitivity. Check with part C. Sensor Placement or H. Superior Set-Up. Lights turn OFF whereas house is occupied. Lights stay ON after area is vacated. Lens does not stop glowing throughout Sensor protection testing even when there isn't a movement. Lights don't respond correctly during wireless communication testing. Sensor lens flashes and lights do not turn on when area is occupied. Battery has been put in incorrectly. An exterior noise source equivalent to an HVAC vent is interfering. Seek advice from part C. Sensor Placement. Discuss with part C. Sensor Placement or F. Testing Wireless Communication. Refer to section H. Superior Set-Up. Discuss with section C. Sensor Placement. Confer with section I. Lens Masking. Refer to part H. Superior Set-Up. Check with section H. Advanced Set-Up. Try moving Sensor to a brand new location or lowering sensitivity. Check with section C. Sensor Placement or H. Advanced Set-Up. Sensor will not be appropriately added to dimming / switching machine. Sensor is exterior wireless vary of dimming/switching machine. Seek advice from section B. Set-Up. Transfer Sensor closer to dimming/switching system and retry take a look at. Check with section F. Testing Wireless Communication. Battery has been installed incorrectly. Dimming/switching gadget has been improperly wired. Light bulb(s) burned out. Breaker is off or tripped. Battery is low. Seek advice from part A. Pre-Installation. Take away sensor from take a look at mode. Consult with section E. Testing Sensor Protection.
Here is my web page: http://www.alexandria.gov.eg/Lists/comp_new/DispForm.aspx?ID=253169